I'm a DIYer swapping out existing switches/receptacles for a different color. I ran across a light switch that had ground wired to neutral instead of the ground connection on the switch. This doesn't make any sense to me but I'm not a pro so maybe I'm missing something?
In Ohio, maybe something in the code here that allows it under certain circumstances? Internet Search is failing me so thought I'd ask.
PS: Duplex receptacle a few feet away has the neutrals cut with tips electrical taped, and ground connected to the neutral terminal. (ಠ_ಠ Confidence in the correctness of the wiring in this area is not very high)